International resources company
Gladstone Region, Brisbane, Australia
Our client located in the Gladstone region encountered a leak in their cooling water system. Two parts of the gasket failed and blew out of the joint.
Leak sealing utilises specialist compounds and a mechanical retaining device to effect a seal. The process combines stringent procedures and risk assessments with experienced trained personnel and specialist equipment to ensure a safe process and an effective seal.
BLJ Gladstone technicians attended the site location and hot bolted the joint, installed injection washers and peened copper wire into the flange gap.
Once the wire was secure in the joint, BLJ technicians injected compound through the injection washers and sealed up the cavity/ leak path. The client was very happy with the result, and BLJ technicians service.